Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Darcy-Weisbach Equation - Major Pressure and Head Loss due to Friction

### Pressure Loss

The pressure loss (or major loss ) in a pipe, tube or duct can be calculated with the Darcy-Weisbach equation

Δp major_loss = λ (l / d h ) (ρ f v 2 / 2) (1)

where

Δp major_loss = major (friction) pressure loss in fluid flow (Pa (N/m 2 ), psf (lb/ft 2 ) )

λ = Darcy-Weisbach friction coefficient

l = length of duct or pipe (m, ft)

v = velocity of fluid (m/s, ft/s)

d h = hydraulic diameter (m, ft)

ρ f = density of fluid (kg/m 3 , slugs /ft 3 )

Note! - be aware that there are two alternative friction coefficients present in the literature. One is 1/4 of the other and (1) must be multiplied with four to achieve the correct result. This is important to verify when selecting friction coefficients from Moody diagrams. The Colebrook friction coefficient calculator corresponds to equation (1).

The Darcy-Weisbach equation is valid for fully developed, steady state and incompressible flow . The friction factor or coefficient - λ -depends on the flow, if it is laminar, transient or turbulent (the Reynolds Number ) - and the roughness of the tube or duct . The friction coefficient can be calculated by the Colebrooke Equation or by using the Moody Diagram .

#### Example - Pressure Loss in Air Duct

Air flows with velocity 6 m/s in a duct with diameter 315 mm . The density of air is 1.2 kg/m 3 . The friction coefficient is estimated to 0.019 and the length of the duct is 1 m . The friction loss can be calculated as

Δp major_loss = 0.019 ((1 m) / (0.315 m)) ((1.2 kg/m 3 ) (6 m/s) 2 / 2)

= 1.3 Pa

Note! - in addition to friction loss - there is almost always minor loss in a flow .

### Online Pressure Loss Calculator

The calculator below, which is based on formula (1), can be used to calculate the pressure loss in a duct, pipe or tube if the velocity of the fluid is known. The default values are for air flow 20 o C , 1.2 kg/m 3 and 6 m/s - the same as in the example above. The friction coefficient can be calculated with the Colebrook equation .

This calculator is generic and can be used with SI and Imperial units. Just substitute the values with the values for the actual application.

The calculator below can be used if the volume flow is known

Alternatively the Darcy-Weisbach equation can express head loss as water column by dividing the pressure loss (1) with the specific weight of water

Δh major_loss,w = λ (l / d h ) (ρ f v 2 / 2) / γ w

= λ (l / d h ) (ρ f v 2 / 2) / ρ w g

= λ (l / d h ) (ρ f / ρ w ) ( v 2 / (2 g)) (2)

where

Δh major_loss,w = major head loss (water column) in fluid flow (m H2O, ft H2O)

λ = friction coefficient

l = length of pipe or duct (m, ft)

d h = hydraulic diameter (m, ft)

v = velocity of fluid (m/s, ft/s)

γ w = ρ w g = specific weight of water (9807 N/m 3 , 62.4 l b f /ft 3 )

ρ w = density of water (1000 kg/m 3 , 62.425 lb/ft 3 )

g = acceleration of gravity (9.81 m/s 2 , 32.174 ft/s 2 )

Note! - in the equation above the head is related to water as the reference fluid. Another reference fluid can be used - like Mercury Hg - by replacing the density of water with the density of the reference fluid.

If the density in the fluid flow is the same as the density in the reference fluid - as typical with water flow - eq. (2) can be simplified to

Δh major_loss = λ (l / d h ) ( v 2 / (2 g)) (2b)

where

Δh major_loss = major head loss (column of flowing fluid) (m "fluid", ft "fluid")

For metric units the head loss can alternatively be modified to

Δh major_loss,w (mmH2O) = λ (l / d h ) (ρ f / ρ w ) ( v 2 / (2 g)) / 1000          (2c)

where

Δh major_loss, w (mmH2O) = head loss (mm H2O)

For imperial units the head loss can alternatively be modified to

Δh major_loss,w (inH2O) = 12 λ (l / d h ) (ρ f / ρ w ) ( < v 2 / (2 g)) (2d)

where

Δh major_loss,w (inH2O) = head loss (inches H2O)

The Darcy-Weisbach equation with the Moody diagram are considered to be the most accurate model for estimating frictional head loss in steady pipe flow. Since the approach requires a trial and error iteration process, an alternative less accurate empirical head loss calculation that do not require the trial and error solutions like the Hazen-Williams equation , may be preferred.

The calculator below, which is based on eq. (2) , can be used to calculate the head loss in a duct, pipe or tube. The default values used in the calculator are for air flow 20 o C , 1.2 kg/m 3 and 6 m/s . The default density of water commonly used as reference fluid is 1000 kg/m 3 . The friction coefficient is calculated with the Colebrook equation .

The calculator is generic and can be used for both SI and Imperial units. Just substitute the values with the values for the actual application.

friction coefficient - λ

length of pipe or duct - l - (m, ft)

hydraulic diameter - d h - (m, inches)

velocity of fluid - v - (m/s, ft/min)

density actual fluid - ρ - (kg/m 3 , lb/ft 3 )

density reference fluid (typical water) - ρ - (kg/m 3 , lb/ft 3 )

SI-units

Imperial units

## Related Topics

### • Fluid Flow and Pressure Loss

Pipe lines - fluid flow and pressure loss - water, sewer, steel pipes, pvc pipes, copper tubes and more.

### • Fluid Mechanics

The study of fluids - liquids and gases. Involving velocity, pressure, density and temperature as functions of space and time.

## Related Documents

### Air Ducts - Friction Loss Diagram

A major friction loss diagram for air ducts - in imperial units ranging 10 000 - 400 000 cfm.

### Air Ducts - Major Friction Loss vs. Temperature and Pressure

The influence of temperature and air pressure on major friction loss.

### ASTM B302 - Threadless Copper Pipes - Dimensions

Dimensions of threadless copper pipes according ASTM B302.

### ASTM B42 - Seamless Copper Pipes - Dimensions

Dimensions of seamless copper pipes according ASTM B42.

### ASTM B837 - Seamless Copper Tubes for Natural Gas and Liquified Petroleum - Dimensions

Dimensions of seamless copper tubes for natural gas and liquified petroleum.

### BS 2871 Copper Tubes Table X, Y and Z - Working Pressures vs. Size

Working pressures of metric sized copper tubes according the BS (British Standard) 2871.

### Colebrook Equation

Friction loss coefficients in pipes, tubes and ducts.

### Copper Tubes Type K, L and M - Working Pressures vs. Size

ASTM B88 seamless copper water tubes - working pressures.

### Energy Equation - Pressure Loss vs. Head Loss

Calculate pressure loss - or head loss - in ducts, pipes or tubes.

### Equivalent Length Method - Minor Pressure Loss in Piping Systems

Calculate minor pressure loss in piping systems with the Equivalent Pipe Length Method.

### Equivalent Length vs. Minor Pressure Head Loss in Pipe and Duct Components

Minor pressure and head loss in pipes vs. equivalent length in tubes and duct systems.

### Fluid Flow - Entrance Length and Developed Flow

The entrance length is the length in a tube or duct after an obstruction - until the flow velocity profile is fully developed.

### Fluid Flow - Hydraulic Diameter

Calculate hydraulic diameter for pipes and ducts.

### Fluid Flow Friction Loss - Hazen-Williams Coefficients

Hazen-Williams friction loss coefficients for commonly used piping materials.

### Hazen-Williams Friction Loss Equation - calculating Head Loss in Water Pipes

Friction head loss (ftH2O per 100 ft pipe) in water pipes can be estimated with the empirical Hazen-Williams equation.

### Hazen-Williams Pressure Loss Equation

The Hazen-Williams equation can be used to calculate the pressure drop (psi) or friction loss in pipes or tubes.

### Laminar Flow - Friction Coefficients

Calculate friction coefficients for laminar fluid flow.

### Laminar, Transitional and Turbulent Flow

Heat transfer, pressure and head loss in a fluid varies with laminar, transitional or turbulent flow.

### Natural Draft - Air Flow Volume and Velocity

Air flow - volume and velocity - due to stack or flue effect caused by indoor hot and outdoor cold temperature difference.

### PE, PEH and PVC Pipes - Pressure Loss vs. Water Flow Diagram

Pressure loss (bar/100 m) and velocy in PE, PEH or PVC pipes with water flow.

### Pipe Equations

Calculate cross-sectional areas, weight of empty pipes, weight of pipes filled with water, inside and outside surface areas.

### Pressure Coefficient

The Pressure Coefficient is the ratio of pressure forces to inertial forces.

Static pressure graphical presentation throughout a fluid flow system.

### Pressure Loss in Pipes connected in Series or Parallel

Calculate pressure loss in pipes connected in series or parallel.

### Pressure to Head Unit Converter

Pressure vs. head units - like lb/in2, atm, inches mercury, bars, Pa and more.

### Reynolds Number

Introduction and definition of the dimensionless Reynolds Number - online calculators.

Static pressure vs. pressure head in fluids.

### Steel Pipes Schedule 40 - Friction Loss vs. Water Flow Diagram

Friction loss and velocity diagrams - in imperial (psi/100 ft, ft/s) and SI (Pa/100m, m/s) units.

### Steel Pipes Schedule 80 - Friction Loss vs. Water Flow Diagram

Water flow in steel pipes schedule 80 - pressure drop and velocity diagrams in SI and Imperial units.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!