Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Air Ducts - Major Friction Loss vs. Temperature and Pressure

Air ducts friction loss and pressure drop diagrams are normally made for air at Normal Temperature and Pressure (NTP) condition - with a temperature of 20 oC and a atmospheric pressure of 1 bar.

### Influence of Temperature

The friction coefficient in the D'Arcy-Weisbach Equation increases with higher temperature but the coefficient will also be outweighed by the reduced pressure loss due to reduced density of the air.

• the pressure loss in an air duct is reduced with higher temperature

With air temperature other than 20 oC - a "Temperature Compensating Coefficient" can be used to modify the pressure loss:

Δp = kt ΔpNTP         (1)

where

Δp = actual friction loss (pressure or head)

kt = Temperature Compensating Coefficient

ΔpNTP = friction loss at NTP conditions (pressure or head)

"Temperature Compensating Coefficient" for various air temperatures:

### Example - Air with Temperature 100oC

For air with temperature 100oC the "Temperature Compensating Coefficient" is approximately 0.83. So,

• the pressure loss in air with temperature 100oC is approximately 83 % of the pressure loss in air at standard NTP conditions 20 oC

### Influence of Pressure

If the actual pressure differ from atmospheric pressure (1 bar abs) - friction loss in air ducts should be compensated with a "Pressure Compensating Coefficient":

Δp = kp ΔpNTP         (2)

where

Δp = actual friction loss (pressure or head)

kp = Pressure Compensating Coefficient

ΔpNTP = friction loss at NTP conditions (pressure or head)

The "Pressure Compensating Coefficient" can be estimated for various pressures from the diagram below:

• 1000 mbar = 1 bar = 105 Pa (N/m2) = 0.1 N/mm2 = 10,197 kp/m2 = 10.20 m H2O = 0.9869 atm = 14.50 psi (lbf/in2) = 106 dyn/cm2 = 750 mmHg

## Related Topics

### • Ventilation

Systems for ventilation and air handling - air change rates, ducts and pressure drops, charts and diagrams and more.

## Related Documents

### Air Ducts - Friction Loss Diagram

A major friction loss diagram for air ducts - SI units.

### Darcy-Weisbach Equation - Major Pressure and Head Loss due to Friction

The Darcy-Weisbach equation can be used to calculate the major pressure and head loss due to friction in ducts, pipes or tubes.

### STP - Standard Temperature and Pressure and NTP - Normal Temperature and Pressure

The definition of STP - Standard Temperature and Pressure and NTP - Normal Temperature and Pressure.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!