# Electric Motors - Efficiency

Electrical motor efficiency is the ratio between shaft output power - and electrical input power.

### Electrical Motor Efficiency when Shaft Output is measured in Watt

If power output is measured in *Watt (W) *then efficiency can be expressed as

η_{m}=P_{out}/ P_{in}(1)

where

η_{m}= motor efficiency

P_{out}= shaft power out (Watt, W)

P_{in}= electric power in to the motor (Watt, W)

### Electrical Motor Efficiency when Shaft Output is measured in Horsepower

If power output is measured in *horsepower (hp)*, efficiency can be expressed as

η_{m}=P_{out}746 / P_{in}(2)

where

P_{out}= shaft power out (horsepower, hp)

P_{in}= electric power in to the motor (Watt, W)

### Primary and Secondary Resistance Losses

The electrical power lost in the primary rotor and secondary stator winding resistance are also called **copper losses**. The copper loss varies with the load in proportion to the current squared - and can be expressed as

P_{cl}= R I^{2}(3)

where

P_{cl}= stator winding - copper loss (W, watts)

R= resistance (Ω)

I= current (A, amps)

### Iron Losses

These losses are the result of magnetic energy dissipated when when the motors magnetic field is applied to the stator core.

### Stray Losses

Stray losses are the losses that remains after primary copper and secondary losses, iron losses and mechanical losses. The largest contribution to the stray losses is harmonic energies generated when the motor operates under load. These energies are dissipated as currents in the copper winding, harmonic flux components in the iron parts, leakage in the laminate core.

### Mechanical Losses

Mechanical losses includes friction in the motor bearings and the fan for air cooling.

### NEMA Design B Electrical Motors

Electrical motors constructed according NEMA Design B must meet the efficiencies below:

Power (hp) | Minimum Nominal Efficiency^{1)} |
---|---|

1 - 4 | 78.8 |

5 - 9 | 84.0 |

10 - 19 | 85.5 |

20 - 49 | 88.5 |

50 - 99 | 90.2 |

100 - 124 | 91.7 |

> 125 | 92.4 |

^{1)} NEMA Design B, Single Speed 1200, 1800, 3600 RPM. Open Drip Proof (ODP) or Totally Enclosed Fan Cooled (TEFC) motors 1 hp and larger that operate more than 500 hours per year.

## Related Topics

### • Electrical

Electrical units, amps and electrical wiring, wire gauge and AWG, electrical formulas and motors.

## Related Documents

### Asynchronous Induction Motors - Electrical Properties

Typical electrical motor data like nominal current, fuse, start ampere, size of contactor and circuit breaker - for asynchronous induction motors.

### Efficiency

The measure of usefulness.

### Efficiency

Efficiency is the ratio useful energy output to energy input.

### Efficiency of Small Machine Elements

Friction and efficiency in bearings and roller chains.

### Electric Motor Calculator

Calculate amps, hp and kVA for electrical motors.

### Electric Motors - 480 Volt Wiring

480V electrical motor wiring data - NEMA amps, starter size, HMCP size for motors ranging 1/2 to 500 hp.

### Electric Motors - Efficiency

Calculate electric motor efficiency.

### Electric Motors - Efficiency

Calculate electric motor efficiency.

### Electrical Induction Motors - Synchronous Speed

Operating speed of an induction motor depends on the input power frequency and the number of magnetic poles in the motor.

### Electrical Motors - Frame Dimensions

Electrical motors NEMA frame dimensions.

### Electrical Motors - Heat Loss

Heat loss from an electrical motor to the surroundings.

### Electrical Motors - Horsepower vs. Voltage and Amps

Electrical motors horsepower rating vs. their ampere rating.

### Electrical Motors - Insulation Classes

Electrical motors NEMA temperature and insulation classes.

### Electrical Motors - Locked Rotor Design Code Letters

NEMA locked rotor indicating code letters for electrical motors.

### Electrical Motors - Service Factors

Service factor - *SF* - is a measure of periodically overload capacity at which a motor can operate without beeing damaged.

### Electrical Motors - Speed at Operating vs. Synchronous Load

Speed of an operating electrical motor with load is lower than the synchronous speed (no load) of the motor.

### Electrical Motors - Speed vs. No. of Poles and Frequency

The speed of electrical motors with 2, 4, 6 or 8 poles at 50 Hz and 60 Hz.

### Electrical Motors - Starting Devices

Direct-on-line starters, star-delta starters, frequency drives and soft starters.

### Heat Gain from Electrical Motors in Continuous Operation

Amount of heat transferred from electrical motor to ambient room vs. locations of fan and motor.

### NEMA - National Electrical Manufacturers Association

National Electrical Manufacturers Association.

### NEMA A, B, C and D Electrical Motor Design

NEMA has established the four different designs A, B, C and D for electrical induction motors.

### Polyphase Motors - Voltage Imbalance vs. Derating Factor

Increased voltage imbalance and decreased efficiency.

### Single Phase Power Equations

Power equations for single phased electrical systems.

### Three-Phase Electrical Motors - Power vs. Amps and Voltage

Full load amps, wire and conduit sizes for three phase electrical motors.

### Three-Phase Power - Equations

Electrical 3-phase equations.