HazenWilliams Friction Loss Equation  calculating Head Loss in Water Pipes
Friction head loss (ft_{H2O} per 100 ft pipe) in water pipes can be estimated with the empirical HazenWilliams equation.
The DarcyWeisbach equation with the Moody diagram is considered to be the most accurate model for estimating frictional head loss for a steady pipe flow. Since the DarcyWeisbach equation requires iterative calculation an alternative empirical head loss calculation like the HazenWilliams equation may be preferred:
h _{ 100ft } = 0.2083 (100 / c)^{1.852 } q^{1.852 } / d^{4.8655 }(1)
where
h _{ 100ft } = friction head loss in feet of water per 100 feet of pipe (ft _{ h20 } /100 ft pipe)
c = HazenWilliams roughness constant
q = volume flow (gal/min)
d = inside diameter of pipe (inches)
Note that the HazenWilliams formula is empirical and lacks a theoretical basis. Be aware that the roughness constants are based on "normal" conditions with approximately 1 m/s (3 ft/sec) .
Example  Friction Head Loss in Water Pipe
200 gal/min of water flows in a 3 inch PEH pipe DR 15 with inside diameter 3.048 inches. The roughness coefficient for PEH pipe is 140 and the length of the pipe is 30 ft. The head loss for 100 ft pipe can be calculated as
h _{ 100ft } = 0.2083 (100 / 140)^{1.852 } (200 gal/min)^{1.852 } / (3.048 in)^{4.8655 }
= 9 ft H_{2}O / 100 ft pipe
The head loss for 30 ft pipe can be calculated
h _{ 30ft } = h _{ 100ft } (30 ft) / (100 ft)
= 9 (30 ft) / (100 ft)
= 2.7 ft H_{2}O
Related Mobile App from The Engineering ToolBox
 free apps for offline use on mobile devices.
Online HazensWilliams Calculator
Imperial Units
The calculators below can used to calculate the specific head loss (head loss per 1 00 ft (m) pipe) and the actual head loss for the actual length of pipe. Default values are from the example above.
SI Units
The HazenWilliams equation is not the only empirical formula available. Manning's formula is commonly used to calculate gravity driven flows in open channels.
The flow velocity can be calculated as
v = 0.408709 q / d^{2}(2)
where
v = flow velocity (ft/s)
Limitations
The HazenWilliams equation is assumed to be relatively accurate for water flow in piping systems when
 the Reynolds Numbers is above 10^{5} ( turbulent flow )
 the water temperature is in the range 40  75 ^{o}F (5  25 ^{o}C) and the kinematic viscosity is approximately 1.1 cSt
For hotter water with lower kinematic viscosity (example 0.55 cSt at 130 ^{o}F (54.4 ^{o}C)) the error will be significant.
Since the HazenWilliams method is only valid for water flow  the Darcy Weisbach method should be used for other liquids or gases.
 1 ft (foot) = 0.3048 m
 1 in (inch) = 25.4 mm
 1 gal (US)/min =6.30888x10 ^{ 5 } m^{3} /s = 0.227 m^{3} /h = 0.0631 dm^{3} (liter)/s = 2.228x10^{3} ft^{3} /s = 0.1337 ft^{3} /min = 0.8327 Imperial gal (UK)/min
Related Topics

Fluid Flow and Pressure Loss in Pipes and Tubes
Fluid flow and pressure loss in pipe lines. Water and sewer systems. Steel pipes, pvc pipes, copper tubes and more. 
Fluid Mechanics
The study of fluids  liquids and gases. Involving velocity, pressure, density and temperature as functions of space and time.
Related Documents

Copper Tubes  Pressure Loss vs. Water Flow
Water flow and pressure loss (psi/ft) due to friction in copper tubes ASTM B88 Types K, L and M. 
DarcyWeisbach Equation  Major Pressure and Head Loss due to Friction
The DarcyWeisbach equation can be used to calculate the major pressure and head loss due to friction in ducts, pipes or tubes. 
Equivalent Length Method  Minor Pressure Loss in Piping Systems
Calculate minor pressure loss in piping systems with the Equivalent Pipe Length Method. 
Fluid Flow Friction Loss  HazenWilliams Coefficients
HazenWilliams friction loss coefficients for commonly used piping materials. 
Friction Loss in Steel, Copper and Plastic Pipes
Friction head loss (ft/100 ft) vs. water flow in steel, copper and PVC plastic pipes. 
HazenWilliams Pressure Loss Equation
The HazenWilliams equation can be used to calculate the pressure drop (psi) or friction loss in pipes or tubes. 
Hot Water Systems  Equivalent Length vs. Fittings Resistance
Equivalent length of fittings like bends, returns, tees and valves in hot water heating systems  equivalent length in feet and meter. 
Lined Pipes  Pressure Loss vs. Water Flow
Pressure drop diagrams for PTFE, PP, PFA and PVDF lined pipes. 
Manning's Formula and Gravity Flow
Calculate crosssectional average velocity flow in open channels. 
Piping Equations
Calculate crosssectional areas, weight of empty pipes, weight of pipes filled with water, inside and outside surface areas. 
Plastic Pipes  Friction Head Loss vs. Water Flow
Friction head loss (ft/100 ft) vs. water flow in plastic pipes like PVC, PP, PE or PEH. 
Pressure Loss in Pipes connected in Series or Parallel
Calculate pressure loss in pipes connected in series or parallel. 
PVC Pipes  Equivalent Length and Pressure Loss in Fittings
Minor loss in PVC and CPVC fittings expressed as equivalent length of straight pipe. 
PVC Pipes Schedule 40  Friction Loss vs. Water Flow
Water flow in thermoplastic PVC and CPVC pipes Schedule 40  friction loss (ft/100 ft, psi/100 ft) and flow velocities at dimensions ranging 1/2 to 16 inches. 
PVC Pipes Schedule 40  Friction Loss vs. Water Flow Diagrams
Friction loss (psi/100 ft) and velocity for water flow in plastic PVC pipe schedule 40. 
Steel Pipes  Maximum Water Flow Capacities vs. Size
Maximum water flow capacities in steel pipes  pipe dimensions ranging 2  24 inches. 
Steel Pipes Schedule 40  Friction Loss vs. Water Flow Diagram
Friction loss and velocity diagrams  in imperial (psi/100 ft, ft/s) and SI (Pa/100m, m/s) units. 
Steel Pipes Schedule 40  Pressure Loss
Water flow and pressure loss in schedule 40 steel pipes  Imperial and SI units  gallons per minute, liters per second and cubic meters per hour. 
Steel Pipes Schedule 80  Friction Loss vs. Water Flow Diagram
Water flow in steel pipes schedule 80  pressure drop and velocity diagrams in SI and Imperial units. 
Water Distribution Pipes  Materials
Materials used in water distribution pipes. 
Water Flow in Tubes  Reynolds Number
Reynolds number for clean cold water flow. 
Water Supply Systems  Online Design Application
Free online tool for designing water supply systems in buildings.