- Resources, Tools and Basic Information for Engineering and Design of Technical Applications!
Expansion of steam pipes heated from room temperature to operation temperature.
Expansion of steam pipes when pressurized and heated from room temperature.
Thermal Expansion of Steam Pipes
Operating Temperature ( oF) Expansion (inches per 100 ft Pipe)
Note! - to avoid unacceptable stress and damage in a steam pipe line - handle expansion properly. Example - Expansion of Steam Pipe
A system is designed for
pressure with operating temperature 120 psi 350 . As indicated in the table above oF (350 the expansion is is approximately oF) 2.4 in pipe. 100ft
The expansion of a
90 ft long pipe can be calculated as
dl = ((2.4 in 100ft) / (100 ft)) (90 ft)
= 2.2 in
Sizing of steam and condensate pipe lines - pressure loss, recommended velocity, capacity and more.
Steam & condensate systems- properties, capacities, pipe sizing, systems configuration and more.
Calculate ring (or pipe) diameter expansion or contraction when temperature changes.
Temperature changes introduces stress fixed pipes.
Online linear temperature expansion calculator.
Thermal expansion coefficients metals.
Pipes expands when heated and contracts when cooled and the expansion can be expressed with the expansion equation.
Temperature expansion coefficients for materials used in pipes and tubes like aluminum, carbon steel, cast iron, PVC, HDPE and more.
Expansion and contraction when cast iron, carbon and carbon molybdenum steel, wrought iron, copper, brass and aluminum pipes are heated or cooled.
Temperature expansion loops with pressfit piping.
Thermal expansion of PVC, CPVC, Carbon and Stainless Steel and Fiberglass pipes.
Stress and force when thermal expansion a pipe, beam or similar is restricted.
Steam is a compressible gas where pipe line mass flow capacity depends on steam pressure.
Steam is a compressible gas where the capacity of a pipe line depends on the size of the pipe and the steam pressure.
Sizing of steam pipe lines - major and minor loss in steam distribution systems.
Thermal expansion of steam pipes heated from room temperature to operation temperature (mm pr. 100 m pipe).
Calculate temperature expansion with carbon steel pipes.
Calculating and sizing steel pipe thermal expansion loops.
Linear temperature expansion coefficients for common materials like aluminum, copper, glass, iron and many more.
About the Engineering ToolBox!
We don't collect information from our users. More about
This page can be cited as
The Engineering ToolBox (2003).
Thermal Expansion of Steam Pipes - . [online] Available at: https://www.engineeringtoolbox.com/temperature-expansion-steam-pipes-d_267.html [Accessed Day Month Year].
Modify the access date according your visit.