Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

Steam Pipes - Sizing

Sizing of steam pipe lines - major and minor loss in steam distribution systems.

The pressure available for distribution of steam is the pressure difference between the initial pressure at the boiler, and the required final pressure at the end of the line - at the steam consumer.

The pressure difference available for the distribution system can be expressed as:

p = pj - pk                                    (1)

where

p = available pressure drop (Pa (N/m2), psi (lb/ft2))

pj = initial or boiler pressure (Pa (N/m2), psi (lb/ft2))

pk = final pressure (Pa (N/m2), psi (lb/ft2))

The total pressure drop in the distribution system is a result of friction (major loss) and pressure loss in fittings (minor loss), and can be expressed as:

pt = pmajor + pminor                               (2)

where

pt = total pressure drop in the system (Pa (N/m2), psi (lb/ft2))

pmajor = pressure loss in pipes due to friction (Pa (N/m2), psi (lb/ft2))

pminor = pressure loss in fittings (Pa (N/m2), psi (lb/ft2))

Friction - Major Loss

Major loss - the pressure loss due to friction in a low pressure steam distribution system can be expressed as:

pmajor = pa l                                (3)

where

pa = pipe friction resistance per unit length of pipe (Pa/m (N/m2/m), psi/ft (lb/ft2/ft))

l = length of pipe (ft, m)

The pressure drop in a steam pipe can be expressed as

pa-100 = 0.01306 q2 (1 + 3.6/di) / (3600ρ di5)                                      (3b)

where

pa-100 = pressure drop per 100 ft pipe (psig / 100 ft)

q = steam flow rate (lb/h)

di = inside diameter of pipe (in)

ρ = density of steam (lb/ft3)

Loss due to Fittings - Minor loss

Loss due to fittings - minor loss can be expressed as:

pminor = ξ 1/2ρ v2                                 (4)

where

ξ = minor loss coefficient

pminor = pressure loss (Pa (N/m2), psi (lb/ft2))

ρ = density (kg/m3, slugs/ft3)

v = flow velocity (m/s, ft/s)

Equivalent length

Minor loss - loss due to fittings can also be expressed as equivalent length:

pminor = pa le                                (5)

or

pt = pa(l + le)                                 (6)

where

le = equivalent length of the fittings (ft, m)

As a rule of thumb the total pressure drop is about 5 -10% of initial pressure per 100 m pipe.

Typical Steam Velocities

• Exhaust steam - 20 to 30 m/s (70 - 100 ft/s)
• Saturated steam - 30 to 40 m/s (100 - 130 ft/s)
• Superheated steam - 40 to 60 m/s (130 -200 ft/s)

Related Topics

• Sizing of Steam and Condensate Pipes

Dimensions of steam and condensate pipe lines. Calculate pressure losses, recommended velocities, capacities and more.
• Steam and Condensate

Design of steam & condensate systems with properties, capacities, sizing of pipe lines, system configuration and more.

Related Documents

• ANSI Schedule 40 Steel Pipes - Dimensions

Internal and external diameters, areas, weights, volumes and number of threads for ANSI schedule 40 steel pipes.
• Condensate Pipe Lines - Sizing

Flow and pressure loss in condensate return lines - SI Units.
• Horizontal Pipe Hanger Supports - Spacing and Rod Size

Recommended maximum support span between hangers - and rod sizes for straight horizontal pipes.
• Insulated Steam Pipes - Condensate Generated (kg/h per 100m)

Heat loss from steam pipes generates condensate which must be drained from the system.
• Recommended Velocities in Steam Systems

The steam velocity in a steam distribution system should be within certain limits to avoid excessive wear and tear
• Sizing Steam Pipes (kg/h)

Steam is a compressible gas where pipe line mass flow capacity depends on steam pressure.
• Sizing Steam Pipes (lb/h)

Steam is a compressible gas where the capacity of a pipe line depends on the size of the pipe and the steam pressure.
• Steam Flow Rate vs. Pressure Drop - Schedule 40 Pipe

Flow rate (lb/h) and pressure drop per 100 feet of pipe.
• Steam Heating Processes - Load Calculating

Calculating the amount of steam in non-flow batch and continuous flow heating processes.
• Steam Heating Systems - Design

An introduction to the basic design of steam heating systems.
• Steam Pipes - Installation of Drip Legs

Properly draining steam pipes for condensate.
• Steam Pipes - Online Pressure drop Calculator

Calculate pressure drops in steam distribution pipe lines.
• Steam Pipes - Pressure Drop vs. Steam Flow

Steam pipes and pressure drop diagrams - imperial and metric units.
• Steam Trap Selection Guide

Steam trap selection guide - Float & Thermostatic, Inverted Bucket, Bimetal Thermostatic, Impulse and Thermodynamic Disc steam traps.
• Steel Pipes - Thermal Expansion Loops

Calculating and sizing steel pipe thermal expansion loops.
• Thermal Expansion of Steam Pipes - (inches)

Expansion of steam pipes heated from room temperature to operation temperature.

Search

Search is the most efficient way to navigate the Engineering ToolBox.

Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with older versions of the amazing SketchUp Make and the newer "up to date" SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp Make/Pro from the Extension Warehouse !

We don't collect information from our users. More about

We use a third-party to provide monetization technologies for our site. You can review their privacy and cookie policy here.

You can change your privacy settings by clicking the following button: .

Citation

• The Engineering ToolBox (2003). Steam Pipes - Sizing. [online] Available at: https://www.engineeringtoolbox.com/steam-pipe-sizing-d_105.html [Accessed Day Month Year].

Modify the access date according your visit.

8.21.8

.