Steam Pipes  Sizing
Sizing of steam pipe lines  major and minor loss in steam distribution systems.
The pressure available for distribution of steam is the pressure difference between the initial pressure at the boiler, and the required final pressure at the end of the line  at the steam consumer.
The pressure difference available for the distribution system can be expressed as:
p = p_{j}  p_{k} (1)
where
p = available pressure drop (Pa (N/m^{2}), psi (lb/ft^{2}))
p_{j} = initial or boiler pressure (Pa (N/m^{2}), psi (lb/ft^{2}))
p_{k} = final pressure (Pa (N/m^{2}), psi (lb/ft^{2}))
The total pressure drop in the distribution system is a result of friction (major loss) and pressure loss in fittings (minor loss), and can be expressed as:
p_{t} = p_{major} + p_{minor} (2)
where
p_{t} = total pressure drop in the system (Pa (N/m^{2}), psi (lb/ft^{2}))
p_{major} = pressure loss in pipes due to friction (Pa (N/m^{2}), psi (lb/ft^{2}))
p_{minor} = pressure loss in fittings (Pa (N/m^{2}), psi (lb/ft^{2}))
Friction  Major Loss
Major loss  the pressure loss due to friction in a low pressure steam distribution system can be expressed as:
p_{major} = p_{a} l (3)
where
p_{a} = pipe friction resistance per unit length of pipe (Pa/m (N/m^{2}/m), psi/ft (lb/ft^{2}/ft))
l = length of pipe (ft, m)
The pressure drop in a steam pipe can be expressed as
p_{a100} = 0.01306 q^{2} (1 + 3.6/d_{i}) / (3600 ρ d_{i}^{5}) (3b)
where
p_{a100} = pressure drop per 100 ft pipe (psig / 100 ft)
q = steam flow rate (lb/h)
d_{i} = inside diameter of pipe (in)
ρ = density of steam (lb/ft^{3})
Loss due to Fittings  Minor loss
Loss due to fittings  minor loss can be expressed as:
p_{minor} = ξ 1/2ρ v^{2} (4)
where
ξ = minor loss coefficient
p_{minor} = pressure loss (Pa (N/m^{2}), psi (lb/ft^{2}))
ρ = density (kg/m^{3}, slugs/ft^{3})
v = flow velocity (m/s, ft/s)
Equivalent length
Minor loss  loss due to fittings can also be expressed as equivalent length:
p_{minor} = p_{a} l_{e} (5)
or
p_{t} = p_{a}(l + l_{e}) (6)
where
l_{e} = equivalent length of the fittings (ft, m)
As a rule of thumb the total pressure drop is about 5 10% of initial pressure per 100 m pipe.
Typical Steam Velocities
 Exhaust steam  20 to 30 m/s (70  100 ft/s)
 Saturated steam  30 to 40 m/s (100  130 ft/s)
 Superheated steam  40 to 60 m/s (130 200 ft/s)
Related Topics

Pipe Sizing
Sizing of steam and condensate pipe lines  pressure loss, recommended velocity, capacity and more. 
Steam and Condensate
Steam & condensate systems properties, capacities, pipe sizing, systems configuration and more.
Related Documents

ANSI Schedule 40 Steel Pipes  Dimensions
Internal and external diameters, areas, weights, volumes and number of threads for ANSI schedule 40 steel pipes. 
Condensate Pipe Lines  Sizing
Flow and pressure loss in condensate return lines  SI Units. 
Horizontal Pipe Hanger Supports  Spacing and Rod Size
Recommended maximum support span between hangers  and rod sizes for straight horizontal pipes. 
Insulated Steam Pipes  Condensate Generated (kg/h per 100m)
Heat loss from steam pipes generates condensate which must be drained from the system. 
Recommended Velocities in Steam Systems
The steam velocity in a steam distribution system should be within certain limits to avoid excessive wear and tear 
Sizing of Steam Pipes (kg/h)
Steam is a compressible gas where pipe line mass flow capacity depends on steam pressure. 
Sizing of Steam Pipes (lb/h)
Steam is a compressible gas where the capacity of a pipe line depends on the size of the pipe and the steam pressure. 
Steam Flow Rate vs. Pressure Drop  Schedule 40 Pipe
Flow rate (lb/h) and pressure drop per 100 feet of pipe. 
Steam Heating Processes  Load Calculating
Calculating the amount of steam in nonflow batch and continuous flow heating processes. 
Steam Heating Systems  Design
An introduction to the basic design of steam heating systems. 
Steam Pipes  Installation of Drip Legs
Properly draining steam pipes for condensate. 
Steam Pipes  Online Pressure drop Calculator
Calculate pressure drops in steam distribution pipe lines. 
Steam Pipes  Pressure Drop vs. Steam Flow
Steam pipes and pressure drop diagrams  imperial and metric units. 
Steam Trap Selection Guide
Steam trap selection guide  Float & Thermostatic, Inverted Bucket, Bimetal Thermostatic, Impulse and Thermodynamic Disc steam traps. 
Steel Pipes  Thermal Expansion Loops
Calculating and sizing steel pipe thermal expansion loops. 
Thermal Expansion of Steam Pipes  inches
Expansion of steam pipes heated from room temperature to operation temperature.