Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

Hot Water Expansion Tanks - Sizing

Expansion tanks are required in heating, cooling or air condition system to avoid unacceptable increases of system pressures when water expands during heat-up.

Explosive Power of Super-heated Water

• 1 lb (0.45 kg) of nitroglycerin > 2 000 000 ft lbf (2 700 000 J)
• 1 lb (0.45 kg) of water flashed into steam > 750 000 ft lbf (100 000 J)

Expansion tanks are in general designed as

• open tanks
• closed compression tanks
• diaphragm tanks

Net expansion volume of water when heated can be expressed as

V net = (v1 / v0 ) - 1                                      (1)

V net = expansion volume of water ( ft3, m3 )

v0 = specific volume of water at initial (cold) temperature (ft3 /lb, m3 /kg)

v1 = specific volume of water at operating (hot) temperature (ft3 /lb, m3 /kg)

.

Open Expansion Tanks

Required volume of an open expansion tank can be expressed as

V et = k V w [(v1 / v0 ) - 1]                                     (2)

V et = required expansion tank volume (gallon, liter)

k = safety factor (approximately 2 is common)

V w = water volume in the system (gallon, liter)

v0 = specific volume of water at initial (cold) temperature (ft3 /lb, m3 /kg)

v1 = specific volume of water at operating (hot) temperature (ft3 /lb, m3 /kg)

Note that in an open expansion tank fresh air is constantly absorbed in the water and tends to corrode the system. Open expansion tanks must also be located above the highest heating element, in general on the top of buildings, where they may be exposed to freezing.

.

Closed Compression Expansion Tanks

Closed compression tanks can be designed as

• adjustable expansion tanks - air is evacuated or injected by automatic valves to the tanks to control system pressures when temperature and expansion of water rises or falls
• pump-pressured cushion tanks - water is evacuated or injected to the systems to compensate for temperature rise or fall
• compression tanks with closed gas volumes - the tanks contains specific volumes of gas which is compressed when temperatures and system volumes increase

Required volume in a closed expansion tank

V et = k V w [( v1 / v0 ) - 1] / [( p a / p0 ) - ( p a / p1 )]                                          (3)

where

p a = atmospheric pressure - 14.7 (psia)

p0 = system initial pressure - cold pressure (psia)

p1 = system operating pressure - hot pressure (psia)

• initial temperature 50 oF
• initial pressure 10 psig
• maximum operating pressure 30 psig
.

Diaphragm Expansion Tanks

Required volume in a diaphragm expansion tank

V et = k V w [( v1 / v0 ) - 1] / [1 - ( p0 / p1 )]                                            (4)

• initial temperature 50 oF
• initial pressure 10 psig
• maximum operating pressure 30 psig
• safety factor aprox. 2
• acceptance factor aprox. 0.5

Example - Volume in Open Expansion Tank

A system with 1000 gallons of water is heated from 68 oF to 176 oF .

Minimum expansion volume in an open expansion tank with a safety factor 2 can be calculated as

V et = 2 (1000 gallons) [((0.01651 ft3 /lb) / (0.01605 ft3 /lb)) - 1]

= 57 (gallons)

Related Topics

• Heating Systems

Design of heating systems - capacities and design of boilers, pipelines, heat exchangers, expansion systems and more.

Related Documents

Closed Expansion Tanks - Volume vs. Temperature and Pressure

Sizing of low temperature closed expansion tanks.

Diaphragm Expansion Tanks

Low temperature diaphragm expansion tank sizing - calculate tank volume and acceptance volume.

Ethylene Glycol Heat-Transfer Fluid Properties

Properties like freezing point, viscosity, specific gravity and specific heat of ethylene glycol based heat-transfer fluids, or brines.

Heat Loss from Buildings

Overall heat transfer loss from buildings - transmission, ventilation and infiltration.

Heating System Flow Rates

Calculate flow rates in heating systems.

Hot Water Heating System - Design Procedure

Hot water heating system design procedure with heat loss, boiler rating, heater units and more.

Hot Water Heating Systems - Flow Temperatures vs. Outside Temperatures

Seasonal effects on hot-water heating systems flow temperatures.

Hot Water Heating Systems - Online Design Application

Free online design tool for designing hot water heating systems - metric units.

Hot Water Heating Systems - Online Design Application, Imperial Units

Online design tool for hot water heating systems.

Hot Water Heating Systems - Pressure Loss in Steel Pipes

Pressure loss nomogram for hot water steel pipes.

Rectangular Tanks - Volumes

Tank volume per foot depth.

Safety Relief Valves - Capacity vs. Pressure

Maximum safety valve free air relief capacity.

Volumetric (Cubic) Thermal Expansion

Volumetric temperature expansion calculator.

Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!