# Equivalent Diameter - Rectangular vs. Circular HVAC Ducts

The equivalent diameter is the diameter of a circular duct or pipe that gives the same pressure loss as an equivalent rectangular duct or pipe.

The table below can be used to compare equivalent diameters for rectangular and round circular ducts. The table is based on the ducts friction loss formula.

The rectangular dimensions and the air flow volume are adapted to the equal friction loss method of sizing ventilation duct systems.

The table below indicates maximum air flow in low and medium pressure loss ducts.

- maximum friction <
*0.1 - 0.2 inches W.G./100 ft* - air velocity <
*1500 - 2000 ft/min (8 - 10 m/s)*

Customized values can be calculated in the top row.

Air flow - q - (Cubic Feet per Minute, cfm)(m ^{3}/s) | Rectangular Duct Sizes(inches)(mm) x (mm) | Equivalent Diameter Round Duct Sizes - d-_{e }(inches)(mm) | Velocity in equivalent round Duct - v - (ft/min)(m/s) | Friction Loss (inH_{2}O / 100 ft duct)(Pa/100m) |
---|---|---|---|---|

() | x () x () | () | () | () |

80 (0.04) | 3 x 7 4 x 5 | 4.9 4.9 | 611 (3.1) | 0.15 |

100 (0.045) | 4 x 6 | 5.33 | 646 (3.28) | 0.16 |

120 (0.05) | 4 x 7 5 x 6 | 5.7 6.0 | 670 (3.57) | 0.15 |

140 (0.063) | 4 x 8 | 6.09 | 691 (3.5) | 0.15 |

150 (0.068) | 3.5 x 10 | 6.26 | 702 (3.6) | 0.15 |

160 (0.07) | 4 x 9 5 x 7 6 x 6 | 6.4 6.4 6.6 | 710 (3.6) | 0.15 |

180 (0.08) | 4 x 10 | 6.74 | 726 (3.69) | 0.15 |

200 (0.09) | 6 x 7 | 7.1 | 732 (3.7) | 0.14 |

230 (0.12) | 4 x 12 | 7.31 | 790 (4.01) | 0.15 |

250 (0.11) | 6 x 8 | 7.55 | 803 (4.08) | 0.15 |

270 (0.1) | 4 x 14 | 7.81 | 811 (4.12) | 0.15 |

300 (0.14) | 5 x 12 6 x 10 7 x 8 | 8.3 8.4 8.2 | 804 (4.1) | 0.14 |

400 (0.18) | 7 x 10 8 x 9 | 9.1 9.3 | 884 (4.5) | 0.15 |

480 | 8 x 10 9 x 9 | 9.8 9.8 | 923 (4.7) | 0.15 |

600 (0.27) | 8 x 12 10 x 10 | 10.7 10.9 | 909 (4.9) | 0.14 |

750 (0.34) | 8 x 14 9 x 12 10 x 11 | 11.5 11.3 11.5 | 1047 (5.3) | 0.15 |

800 (0.36) | 8 x 15 10 x 12 | 11.8 12.0 | 1048 (5.3) | 0.15 |

1000 (0.45) | 10 x 14 12 x 12 | 12.9 13.1 | 1104 (5.6) | 0.15 |

1300 (0.59) | 12 x 14 | 14.1 | 1189 (6.0) | 0.15 |

1400 (0.63) | 12 x 15 | 14.6 | 1197 (6.1) | 0.15 |

1700 (0.77) | 10 x 22 14 x 15 | 15.9 15.8 | 1231 (6.3) | 0.14 |

1900 (0.86) | 12 x 19 14 x 16 | 16.4 16.4 | 1295 (6.6) | 0.15 |

2000 (0.9) | 10 x 25 12 x 20 15 x 16 | 16.9 16.8 16.9 | 1291 (6.6) | 0.14 |

2500 (1.13) | 14 x 20 15 x 18 | 18.2 17.9 | 1381 (7.0) | 0.15 |

2800 (1.26) | 12 x 26 16 x 20 | 19.0 19.5 | 1428 (7.3) | 0.15 |

3300 (1.49) | 12 x 30 14 x 25 | 20.2 20.2 | 1480 (7.5) | 0.15 |

3800 (1.71) | 12 x 34 15 x 25 | 21.4 21.0 | 1525 (7.8) | 0.15 |

4100 (1.84) | 12 x 36 16 x 25 20 x 20 | 21.9 21.7 21.9 | 1565 (8.0) | 0.15 |

5400 (2.43) | 12 x 45 16 x 30 20 x 24 | 24.1 23.7 23.9 | 1699 (8.6) | 0.15 |

6200 (2.79) | 16 x 36 18 x 30 23 x 25 | 24.7 25.2 26.2 | 1719 (8.7) | 0.15 |

7200 (3.24) | 16 x 40 20 x 32 25 x 25 | 27.0 27.5 27.3 | 1816 (9.2) | 0.15 |

8400 (3.78) | 20 x 35 25 x 28 | 28.6 28.9 | 1879 (9.5) | 0.15 |

10300 (4.64) | 16 x 55 20 x 43 25 x 38 | 31.0 31.5 33.5 | 1964 (10.0) | 0.15 |

13000 (5.85) | 20 x 50 30 x 32 | 33.7 33.9 | 2098 (10.7) | 0.15 |

13500 (6.08) | 20 x 55 30 x 35 | 35.2 35.4 | 2002 (10.2) | 0.13 |

15000 (6.75) | 25 x 48 30 x 40 | 37.4 37.8 | 1969 (10) | 0.12 |

17000 (7.65) | 32 x 40 | 39.1 | 2044 (10.4) | 0.12 |

19000 (8.55) | 32 x 45 35 x 40 | 41.3 40.9 | 2039 (10.4) | 0.11 |

*1 in = 25.4 mm**1 inH*_{2}O / 100 ft = 84 mmH_{2}O /100 m

**Note! - **due to larger circumference and more friction area related to air volume - a circular duct is always more efficient than a rectangular duct.

### Example - Air Flow in Rectangular vs. Circular Duct

*2000 cfm (0.94 m ^{3}/s)* of air flows through a

*10 x 12 inches*rectangular duct.

The friction loss according the table above is *0.81 inches water gauge per 100 ft duct (aprox. 6.6 Pa/m).*

The velocity in the rectangular duct is

*v = (2000 cfm) / (((10 inches) (1/12 ft/inches) ((12 inches)(1/12 ft/inches)))*

* = 2400 ft/min (12.2 m/s)*

The velocity in the the equivalent *12 inch* circular duct according the table above is *2589 ft/min (13.2 m/s)*.

## Related Topics

### • Air Conditioning

Air Conditioning systems - heating, cooling and dehumidification of indoor air for thermal comfort.

### • Ventilation

Systems for ventilation and air handling - air change rates, ducts and pressure drops, charts and diagrams and more.

## Related Documents

### Air Ducts - Friction Loss Diagram

A major friction loss diagram for air ducts - Imperial units ranging *10 - 100 000 cfm*.

### Air Ducts - Friction Loss Diagram

A major friction loss diagram for air ducts - SI units.

### Air Ducts - Major Friction Head Loss, Online Calculator

Head loss or major loss in air ducts - equations and online calculator for rectangular and circular ducts - Imperial and SI units.

### Duct Sizing - the Equal Friction Method

The equal friction method for sizing air ducts is easy and straightforward to use.

### Ducts - Cross-Sectional Area vs. Diameter

Circular ducts sross-sectional areas.

### Ducts - Sheet Metal Gauges

Thickness of sheet metal used in ductwork.

### Ducts or Pipes through Steel Joists - Maximum Sizes

Maximum sizes of ducts or pipes through K series joists.

### Ducts Sizing - the Velocity Reduction Method

The velocity reduction method can be used when sizing air ducts.

### Ductwork - Seal Classes

Ductwork air leakage classes.

### Equivalent Length Method - Minor Pressure Loss in Piping Systems

Calculate minor pressure loss in piping systems with the Equivalent Pipe Length Method.

### Fluid Flow - Equivalent Diameter

Convert rectangular and oval duct geometry to a equivalent circular diameter - online calculator with imperial and SI-units.

### Rectangular Air Ducts - Velocity Diagram

Velocity diagram for rectangular air ducts - metric units.

### Rectangular Ducts - Dimensions

Commonly used metric dimensions for rectangular air ducts in ventilation systems.

### Spiral Ducts - Dimensions

Standard dimensions of spiral ducts - Imperial units.

### Velocity Classification of Ventilation Ducts

Recommended air velocities in ventilation ducts