Latent Heat Flow
Latent heat is the heat when supplied to or removed from air results in a change in moisture content  the temperature of the air is not changed.
Latent Heat Flow  English (Imperial) units
The latent heat flow due to moisture in air can be expressed in English (Imperial) units as
Q_{l} = 60 h_{we} ρ q Δx (1)
where
Q_{l} = latent heat flow (Btu/hr)
h_{we} = 1060  latent heat of vaporization of water (Btu/lb)
ρ = 0.075  air density at standard conditions (lb/ft^{3})
q = measured air flow (ft^{3}/min)
Δx = difference in humidity ratio (lb_{h2o}/lb_{dry_air})
Latent Heat Flow  SIUnits
The latent heat flow due to moisture in air can be expressed in SIunits (metric) as
Q_{l} = h_{we} ρ q Δx / 3600 (2)
where
Q_{l} = latent heat flow (kW)
h_{we} = latent heat of vaporization of water (2454 kJ/kg  in air at atmospheric pressure and 20^{o}C)
ρ = air density at standard conditions (1.202* kg/m^{3})
q = air flow (m^{3}/hr)
Δx = difference in humidity ratio (kg_{h2o}/kg_{dry_air})
*Note that properties of air changes with temperature. Interpolate values if necessary.
Example  Latent Heat Flow
A ventilation system transports 10000 m^{3}/h of air through a building.
The state of the makeup (supply) air is 0 ^{o}C and 100% relative humidity. From the Mollier diagram the humidity ratio  x  can be estimated to 0.0037 (kg_{h2o}/kg_{dry_air}).
The state of the room air is 20 ^{o}C and 40% relative humidity. From the Mollier diagram the humidity ratio can be estimated to 0.0057 (kg_{h2o}/kg_{dry_air}).
The latent heat flow can be calculated as
Q_{l} = (2465.56 kJ/kg) (1.202 kg/m^{3}) (10000 m^{3}/h) ((0.0057 (kg_{h2o}/kg_{dry_air}))  (0.0037 (kg_{h2o}/kg_{dry_air}))) / 3600
= 16.5 kW
Related Topics

Air Psychrometrics
Moist and humid air  psychrometric charts, Mollier diagrams, aircondition temperatures and absolute and relative humidity and moisture content.
Related Documents

Air  Density, Specific Weight and Thermal Expansion Coefficient vs. Temperature and Pressure
Online calculator, figures and tables showing density, specific weight and thermal expansion coefficients of air at temperatures ranging 100 to 1600 °C (140 to 2900 °F) at atmospheric and higher pressure  Imperial and SI Units. 
Air  Humidity Ratio
The mass of water vapor present in moist air  to the mass of dry air. 
Air Heating Systems
Air heating buildings  heat supply vs. air flow and temperature. 
Cooling and Heating Equations
Latent and sensible cooling and heating equations  imperial units. 
Cooling Load  Latent and Sensible Heat
Latent and sensible cooling loads to consider when designing HVAC systems. 
Great Sensible Heat Factor  GSHF
The Great Sensible Heat Factor is the ratio sensible to total heat in a cooling coil. 
Heat Recovery Efficiency
Classification of heat recovery efficiencies  temperature efficiency, moisture efficiency and enthalpy efficiency  online heat exchanger efficiency calculator. 
Humid Air  Heating
Enthalpy change and temperature rise when heating humid air without adding moisture. 
Liquids  Latent Heat of Evaporation
Latent heat of vaporization for fluids like alcohol, ether, nitrogen, water and more. 
Melting and Boiling Temperatures  Evaporation and Melting Heats common Materials
Melting and boiling point temperatures, latent heat of evaporation, and melting heat of common substances like copper, gold, lead and more  SI units. 
Moist Air  Enthalpy
Sensible and latent heat of moist air. 
Propane  Latent Heat of Vaporization vs. Temperature
Latent heat with vaporized propane. 
Removing Heat with Air
Calculating heat removed with air by measuring the wet bulb temperature. 
Room Sensible Heat Factor  RSHF
Room Sensible Heat Factor  RSHF  is defined as the sensible heat load divided by the total heat load in a room 
Saturated Steam  Properties for Pressure in Bar
Saturated Steam Table with properties like boiling point, specific volume, density, specific enthalpy, specific heat and latent heat of vaporization. 
Saturated Steam  Properties with Imperial Units
Steam table with sensible, latent and total heat, and specific volume at different gauge pressures and temperatures. 
Sensible Heat Flow
Sensible heat is dry heat causing change in temperature but not in moisture content 
Sensible Heat Ratio  SHR
The ratio Sensible Heat (or Cooling) Load to the Total Heat (or Cooling) Load. 
Steam and Vapor Enthalpy
Vapor and steam enthalpy, specific enthalpy of saturated liquid, saturated vapor and superheated vapor. 
Water  Thermophysical Properties
Thermal properties of water at different temperatures like density, freezing temperature, boiling temperature, latent heat of melting, latent heat of evaporation, critical temperature and more.