Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

This is an AMP page - Open full page! for all features.

• the most efficient way to navigate the Engineering ToolBox!

# Room Sensible Heat Factor - RSHF

The Room Sensible Heat Factor - RSHF - expresses the ratio between sensible heat load and total heat load in a room. It can be expressed as:

RSHF = Qsr / Qtr                           (1)

where

RSHF = room sensible heat factor

Qsr = sensible heat load in room (kW, Btu/hr)

Qtr = total heat load in room (kW, Btu/hr)

(1) can be modified to:

RSHF = cp (tr - ti) / (hr - hi)                                 (2)

where

cp = specific heat air (kJ/kg.oC)

tr = room temperature (oC)

ti = inlet temperature (oC)

hr = room enthalpy (kJ/kg)

hi = inlet enthalpy (kJ/kg)

### Example - Room Sensible Heat Factor - RSHF

The sensible heat generated within a room is 4 kW. The latent heat generated is 1.4 kW.

The Room Sensible Heat Factor can be calculated as:

RSHF = (4 kW) / ((4 kW) + (1.4 kW))

= 0.75

## Related Topics

### • Air Psychrometrics

Moist and humid air - psychrometric charts, Mollier diagrams, air-condition temperatures and absolute and relative humidity and moisture content.

## Related Documents

### Air - Thermophysical Properties

Thermal properties of air at different temperatures - density, viscosity, critical temperature and pressure, triple point, enthalpi and entropi, thermal conductivity and diffusivity and more.

### Cooling and Heating Equations

Latent and sensible cooling and heating equations - imperial units.

### Cooling Load - Latent and Sensible Heat

Latent and sensible cooling loads to consider when designing HVAC systems.

### Great Sensible Heat Factor - GSHF

The Great Sensible Heat Factor is the ratio sensible to total heat in a cooling coil.

### Heat Index

Equivalent heat index vs. air temperature and relative humidity - in degrees Fahrenheit and Celsius.

### Human Heat Gain

Heat gain from persons in air conditioned spaces - in btu/hr.

### Indoor Relative Humidity vs. Outdoor Relative Humidity and Temperature

Recommended indoor relative humidity vs. outdoor relative humidity and temperature.

### Latent Heat Flow

Latent heat is the heat when supplied to or removed from air results in a change in moisture content - the temperature of the air is not changed.

### Metabolic Heat Gain from Persons

Human metabolic heat gain in air conditioned rooms.

### Sensible Heat Flow

Sensible heat is dry heat causing change in temperature but not in moisture content

### Sensible Heat Ratio - SHR

The ratio Sensible Heat (or Cooling) Load to the Total Heat (or Cooling) Load.

## Search Engineering ToolBox

• the most efficient way to navigate the Engineering ToolBox!

## SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!