ξ = minor loss coefficient
Δ p minor_loss = minor pressure loss (Pa (N/m 2 ), psf (lb/ft 2 ) )
ρ f = density of fluid (kg/m 3 , slugs /ft 3 )
v = flow velocity (m/s, ft/s)
Minor loss coefficients for commonly used pipe and tube system components:
|Type of Component or Fitting|| Minor Loss Coefficient |
- ξ -
|Tee, Flanged, Dividing Line Flow||0.2|
|Tee, Threaded, Dividing Line Flow||0.9|
|Tee, Flanged, Dividing Branched Flow||1.0|
|Tee, Threaded , Dividing Branch Flow||2.0|
|Elbow, Flanged Regular 90 o||0.3|
|Elbow, Threaded Regular 90 o||1.5|
|Elbow, Threaded Regular 45 o||0.4|
|Elbow, Flanged Long Radius 90 o||0.2|
|Elbow, Threaded Long Radius 90 o||0.7|
|Elbow, Flanged Long Radius 45 o||0.2|
|Return Bend, Flanged 180 o||0.2|
|Return Bend, Threaded 180 o||1.5|
|Globe Valve, Fully Open||10|
|Angle Valve, Fully Open||2|
|Gate Valve, Fully Open||0.15|
|Gate Valve, 1/4 Closed||0.26|
|Gate Valve, 1/2 Closed||2.1|
|Gate Valve, 3/4 Closed||17|
|Swing Check Valve, Forward Flow||2|
|Ball Valve, Fully Open||0.05|
|Ball Valve, 1/3 Closed||5.5|
|Ball Valve, 2/3 Closed||200|
|Diaphragm Valve, Open||2.3|
|Diaphragm Valve, Half Open||4.3|
|Diaphragm Valve, 1/4 Open||21|
The minor loss a ball valve with flow velocity 2 m/s with water with density 1000 kg/m 3 can be calculated as
Δ p minor_loss = (5.5) (1000 kg/m 3 ) (2 m/s) 2 / 2
= 11000 Pa
= 11 kPa
Pipe lines - fluid flow and pressure loss - water, sewer, steel pipes, pvc pipes, copper tubes and more.
The study of fluids - liquids and gases. Involving velocity, pressure, density and temperature as functions of space and time.
Minor loss (pressure or head loss) coefficients for air duct components.
Minor loss coefficient diagrams for air ductwork, bends, expansions, inlets and outlets - SI units.
Calculate pressure loss - or head loss - in ducts, pipes or tubes.
Calculate minor pressure loss in piping systems with the Equivalent Pipe Length Method.
Minor pressure and head loss in pipes vs. equivalent length in tubes and duct systems.
Minor pressure loss with fittings in piping heating systems.
Equivalent length of fittings like bends, returns, tees and valves in hot water heating systems - equivalent length in feet and meter.
Major and minor loss in pipes, tubes and duct systems.
Static pressure graphical presentation throughout a fluid flow system.
Minor loss in PVC and CPVC fittings expressed as equivalent length of straight pipe.
Minor pressure or head loss in ventilation ducts vs. air velocity - minor loss coefficient diagram.
Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with the amazing, fun and free SketchUp Make and SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp from the Sketchup Extension Warehouse!
We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.
Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.