Belt driven fans are used in heating, ventilation, air-conditioning and cooling (HVAC) systems.
The speed of a fan wheel versus the speed of the motor with a belt drive can be calculated as
df nf = dm nm (1)
df = pulley diameter fan (inch, mm)
nf = speed of fan (rpm - rounds per minute)
dm = pulley diameter motor (inch, mm)
nm = speed of motor (rpm - rounds per minute)
Example - Speed of Fan
A synchronous electrical motor rotates with speed 1000 rpm. The motor pulley diameter is 76.5 mm and the fan pulley diameter is 205.5 mm. The speed of the fan can be calculated by modifying (1) to
nf = dm nm / df
- or with values:
nf = (76.5 mm) (1000 rpm) / (205.5 mm)
= 372 rpm
Systems for ventilation and air handling - air change rates, ducts and pressure drops, charts and diagrams and more.
Calculate length and speed of belt and belt gearing.
Friction and efficiency in bearings and roller chains.
The motor must be capable of accelerating the fan wheel to it's operating speed.
Guide to troubleshooting fan problems.
Pulley (Sheave) selection charts for motors ranging 850 - 3450 rpm.
Pulleys, blocks and tackles.