Static Pressure vs. Head
Static pressure vs. pressure head in fluids.
Pressure indicates the normal force per unit area at a given point acting on a given plane. Since there is no shearing stresses present in a fluid at rest  the pressure in a fluid is independent of direction.
For fluids  liquids or gases  at rest the pressure gradient in the vertical direction depends only on the specific weight of the fluid.
How pressure changes with elevation in a fluid can be expressed as
Δp =  γ Δh (1)
where
Δp = change in pressure (Pa, psi)
Δh = change in height (m, in)
γ = specific weight of fluid (N/m^{3}, lb/ft^{3})
The pressure gradient in vertical direction is negative  the pressure decrease upwards.
Specific Weight
Specific Weight of a fluid can be expressed as:
γ = ρ g (2)
where
ρ = density of fluid (kg/m^{3}, slugs/ft^{3})
g = acceleration of gravity (9.81 m/s^{2}, 32.174 ft/s^{2})
In general the specific weight  γ  is constant for fluids. For gases the specific weight  γ  varies with elevation (and compression).
The pressure exerted by a static fluid depends only upon
 the depth of the fluid
 the density of the fluid
 the acceleration of gravity
Static Pressure in a Fluid
For a incompressible fluid  as a liquid  the pressure difference between two elevations can be expressed as:
Δp = p_{2}  p_{1}
=  γ (h_{2}  h_{1}) (3)
where
p_{2} = pressure at level 2 (Pa, psi)
p_{1} = pressure at level 1 (Pa, psi)
h_{2} = level 2 (m, ft)
h_{1} = level 1 (m, ft)
(3) can be transformed to:
Δp = p_{1}  p_{2}
= γ (h_{2}  h_{1}) (4)
or
p_{1}  p_{2} = γ Δh (5)
where
Δh = h_{2}  h_{1} = difference in elevation  the dept down from location h_{2} to h_{1} (m, ft)
or
p_{1} = γ Δh + p_{2} (6)
Example  Pressure in a Fluid
The absolute pressure at water depth of 10 m can be calculated as:
p_{1} = γ Δh + p_{2}
= (1000 kg/m^{3}) (9.81 m/s^{2}) (10 m) + (101.3 kPa)
= (98100 kg/ms^{2} or Pa) + (101300 Pa)
= 199400 Pa
= 199.4 kPa
where
ρ = 1000 kg/m^{3}
g = 9.81 m/s^{2}
p_{2} = pressure at surface level = atmospheric pressure = 101.3 kPa
The gauge pressure can be calculated by setting p_{2} = 0
p_{1} = γ Δh + p_{2}
= (1000 kg/m^{3}) (9.81 m/s^{2}) (10 m)
= 98100 Pa
= 98.1 kPa
Pressure vs. Head
(6) can be transformed to:
Δh = (p_{2}  p_{1}) / γ (7)
Δh express head  the height difference of a column of fluid of specific weight  γ  required to give a pressure difference Δp = p_{2}  p_{1}.
Example  Pressure vs. Head
A pressure difference of 5 psi (lb_{f}/in^{2}) is equivalent to head in water
(5 lb_{f}/in^{2}) (12 in/ft) (12 in/ft) / (62.4 lb/ft^{3})
= 11.6 ft of water
or head in Mercury
(5 lb_{f}/in^{2}) (12 in/ft) (12 in/ft) / (847 lb/ft^{3})
= 0.85 ft of mercury
Specific weight of water is 62.4 (lb/ft^{3}) and specific weight of mercury is 847 (lb/ft^{3}).
Related Topics

Fluid Mechanics
The study of fluids  liquids and gases. Involving velocity, pressure, density and temperature as functions of space and time. 
Pumps
Piping systems and pumps  centrifugal pumps, displacement pumps  cavitation, viscosity, head and pressure, power consumption and more.
Related Documents

DarcyWeisbach Equation  Major Pressure and Head Loss due to Friction
The DarcyWeisbach equation can be used to calculate the major pressure and head loss due to friction in ducts, pipes or tubes. 
Efficiency in Pumps or Fans
The overall pump and fan efficiency is the ratio power gained by the fluid to the shaft power supplied. 
Hydropower
Power potential vs. head and flow rate. 
Hydrostatic Pressure vs. Depth
Depth and hydrostatic pressure. 
PE, PEH and PVC Pipes  Pressure Loss vs. Water Flow Diagram
Pressure loss (bar/100 m) and velocy in PE, PEH or PVC pipes with water flow. 
Potential Energy  Hydropower
Elevation and potential energy in hydropower. 
Pressure Gradient Diagrams
Static pressure graphical presentation throughout a fluid flow system. 
Pressure to Head Unit Converter
Pressure vs. head units  like lb/in^{2}, atm, inches mercury, bars, Pa and more. 
Pumps  Head vs. Pressure
Converting head (ft or m) to pressure (psi or bar, kg/cm^{2}) and vice versa. 
Pumps  NPSH (Net Positive Suction Head)
An introduction to pumps and the Net Positive Suction Head (NPSH). 
Pumps  Parallel vs. Serial Arrangement
Adding head and flowrate for pumps arranged in parallel vs. serial. 
Pumps  Suction Head vs. Altitude
The suction head of a water pump is affected by its operating altitude. 
Pumps and Fans  Energy Equation and Head Rise
The energy equation can be used to calculate the head rise in pumps and fans. 
System Curve and Pump Performance Curve
Utilize the system curve and the pump performance curve to select the proper pump for a particular application. 
Types of Fans  Capacity Ranges
Centrifugal, axial and propeller fans and their capacity ranges. 
Velocity Pressure Head
Dynamic pressure or velocity head. 
Water Pressure vs. Head
Pressure in pounds per square inch (psi) vs. head in feet of water (ft_{h2o}).