Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

## Calculating chiller and cooling tower refrigeration loads - in tons.

Cooling towers tons pairs the water-cooled chiller tons and the water-cooled condenser tons.

### Chiller Refrigeration Tons

The process of cooling is called refrigeration. For commercial and industrial refrigeration systems most of the world uses the kilowatt (kW) as the basic unit of refrigeration. Some commercial and industrial refrigeration systems are rated in Tons of Refrigeration (TR, tons).

A water-chiller refrigeration ton is defined as:

1 Refrigeration Ton (RT) = 1 TONS cond = 12000 Btu /h = 200 Btu /min = 3025.9 k Calories /h = 12661 kJ/h = 3.517 kW

1 kW = 0.2843 Refrigeration Ton (RT)

A ton is the amount of heat removed by an air conditioning system that would melt 1 ton (2000 lbs.) of ice in 24 hours. The heat required to melt 1 lb of ice at 32 o F to water is 144 Btu.

1 Ton Refrigeration = (2000 lb) (144 Btu/lb) / (24 hr)

= 12000 Btu/hr

#### Converting between Btu/h and Tons of Refrigeration

Converting between kW, Btu/h and Tons of Refrigeration
Btu/hRefrigeration TonkW
6000 1/2 1.76
12000 1 3.52
18000 1 1/2 5.28
24000 2 7.03
30000 2 1/2 8.79
36000 3 10.6
42000 3 1/2 12.3
48000 4 14.1
54000 4 1/2 15.8
60000 5 17.6

### Cooling Tower Tons

A cooling tower ton is defined as:

1 cooling tower ton = 1 TONS evap = 1 TONS cond x 1.25 = 15000 Btu /h = 3782 k Calories /h = 15826 kJ/h = 4.396 kW

The equivalent ton on the cooling tower side actually rejects about 15000 Btu/h due to the heat-equivalent of the energy needed to drive the chiller's compressor. This equivalent ton is defined as the heat rejection in cooling 3 U.S. gallons/minute (1500 pound/hour) of water 10°F , which amounts to 15000 Btu/hour , or a chiller coefficient-of-performance ( COP ) of 4.0 - a COP equivalent to an energy efficiency ratio ( EER ) of 13.65 .

### Heat Load and Water Flow

A water systems heat load in Btu/h can be simplified to:

h = c p ρ q dt

= (1 Btu/lb m o F) ( 8.33 lb m /US gal) q (60 min/h) dt

= 500 q dt (1)

where

c p = specific heat, 1 (Btu/lb m o F) for water

ρ = 8.33 (lb m /US gal) for water

q = water volume flow rate (US gal/min)

dt = temperature difference ( o F)

### Example - Water Chiller Cooling

Water flows with 1 gal/min and 10 o F temperature difference. The ton of cooling load can be calculated as:

h = 500 (1 US gal/min) (10 o F)

= 5000 Btu/h

= (5000 Btu/h) / (12000 Btu/ton)

= 0.42 ton

(ft 2 /ton)
Arenas 150 - 200
Classroom 200 - 250
Clean room 100 - 300
Conference room 100 - 200
Data room 80 - 100
Meeting room 200 - 250
Office 300 - 350
Residence 600 - 700

## Related Topics

• ### Air Conditioning

Air Conditioning systems - heating, cooling and dehumidification of indoor air for thermal comfort.

## Related Documents

• ### Air Conditioner Efficiency

The ratio between heat removed and power (watt) used - EER and SEER.
• ### Chilled Water Systems

Chilled water system equations - evaporator and condenser flow rates.
• ### Cooling Load - Convert between kW/ton to COP or EER

Convert between cooling load units like kW/ton, COP and EER.
• ### Cooling Power vs. Airflow and Duct Sizes

Typical relations between cooling power (tons cooling), air flow and duct size
• ### Cooling Tower Efficiency

Maximum cooling tower efficiency is limited by the cooling air wet-bulb temperature.
• ### Cooling Water - Pipe Lines

Sizing cooling water pipe lines - maximum allowable flow, velocity and pressure drops.
• ### Heat Loss from Electrical Equipment

Heat loss from electrical equipment like switch-gear, transformers and variable frequency drives.
• ### Heat Pumps - Performance and Efficiency Ratings

Performance and efficiency rating of heat pumps.
• ### Refrigeration Formulas

Calculate compression work, coefficients of performance and more.
• ### Refrigeration Machinery - Required Ventilation

Ventilation required for refrigeration machinery and compressors in hot areas.
• ### Water Evaporator and Condenser Equations

Air conditioner heat loads and evaporator and condenser water flow rates.

## Search

Search is the most efficient way to navigate the Engineering ToolBox.

## Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with older versions of the amazing SketchUp Make and the newer "up to date" SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp Make/Pro from the Extension Warehouse !

We don't collect information from our users. More about

## Citation

• The Engineering ToolBox (2004). Calculating Cooling Loads. [online] Available at: https://www.engineeringtoolbox.com/cooling-loads-d_665.html [Accessed Day Month Year].

Modify the access date according your visit.

12.8.9