Moist Air  Cooling and Dehumidifying
Cooling and dehumidifying processes of moist and humid air  sensible and latent cooling.
When cooling air  part of the energy is used to separate the water (latent heat), and the rest is used to lower the air temperature (sensible heat).
Cooling Moist Air  Sensible Cooling
If the temperature on a cooling surface  t_{C}  is above or equal to the dew point temperature  t_{DP}  of the surrounding air, the air will be cooled without any change in specific humidity. It is Sensible Heat  the "temperature heat"  in the air that is removed.
The air cools along a constant specific humidity  x  line as indicated in the Mollier diagram below:
The process is very similar (opposite direction) to the sensible heating process and the heating formulas can be adapted to calculate change in enthalpy and temperature.
Note! The specific humidity is constant but the relative humidity will increase.
Dehumidifying Moist Air  Latent Cooling
If the temperature on a cold surface is lower than the dew point temperature  t_{DP}  of the humid air, vapor in the air condensates on the surface. Latent heat  vapor  is removed from the humid air.
This process is indicated in the Mollier diagram as below. The air cools in the direction of point C, which is the intersection point of the cold surface temperature (the cooling surface dew point temperature or the apparatus dewpoint  t_{ADP}) and the saturation line.
With a cold surface of unlimited size and a very small amount of air, it would be possible to reach point C. In the real world a limited surface is never 100% effective and the final state of the cooled and dehumidified air will be somewhere on the straight line between point A and C  point B.
The amount of condensated vapor will be the difference in specific humidity x_{A}  x_{B}.
Note! This process decreases the specific humidity and increases the relative humidity.
Contact Factor  β
The efficiency of a cooling coil can be expressed with the Contact Factor  β  as
β = (x_{A}  x_{B}) / (x_{A}  x_{C})
= (h_{A}  h_{B}) / (h_{A}  h_{C})
≈ (t_{A}  t_{B}) / (t_{A}  t_{C}) (1)
where
β = Contact Factor
x = specific humidity (kg/kg)
h = enthalpy (kJ/kg)
t = temperature (^{o}C)
Bypass Factor  BPF
The Bypass Factor  BPF  (or BF) is also used to express cooling coil efficiency as
BPF = (h_{B}  h_{C}) / (h_{A}  h_{C})
= (t_{B}  t_{C}) / (t_{A}  t_{C})
= (x_{B}  x_{C}) / (x_{A}  x_{C}) (2)
where
BPF = Bypass Factor (BF)
The relationship between the Contact Factor and the Bypass Factor can be expressed as
BPF = 1  β (3)
Heat Flow in a Cooling Coil
The total heat flow rate through a cooling coil can be calculated as
q = m (h_{A}  h_{B}) (4)
where
q = heat flow rate (kJ/s, kW)
m = mass flow rate of air (kg/s)
The total heat flow can be expressed as
q_{s} = v ρ (h_{A}  h_{B}) (4a)
where
v = volume flow (m^{3}/s)
ρ = density of air (kg/m^{3})
Note! The density of air varies with temperature. At 0^{o}C and atmospheric pressure the density is 1.293 kg/m^{3}. At 80^{o}C the density is 1.0 kg/m^{3}.
The total heat flow rate can be split into sensible and latent heat. The sensible heat flow rate can be expressed as
q_{s} = m c_{p} (t_{A}  t_{B}) (4b)
where
c_{p} = 1.01  specific heat air (kJ/kg^{o}C)
The latent heat flow rate can be expressed as
q_{s} = m h_{we} (x_{A}  x_{B}) (4c)
where
h_{we} = water evaporation enthalpy (2502 kJ/kg)
Example  Cooling and Dehumidifying Air
1 m^{3}/s of air at 30 ^{o}C (86 ^{o}F) and relative humidity 60% (A) is cooled down to 15 ^{o}C (59 ^{o}F) (B). The surface temperature of the cooling coil is 0 ^{o}C (32 ^{o}F) (C). The density of the air at 20 ^{o}C is 1.205 kg/m^{3}.
In the Mollier diagram the state of the cooled air (B) is in the intersection between the straight line between (A) and (C) and the 15 ^{o}C temperature line.
From the Mollier diagram it can be stated that the enthalpy in (A) is 70 kJ/kg, in (B) 38.5 kJ/kg and in (C) 8.5 kJ/kg.
The Contact Factor can be calculated as
β = ((70 kJ/kg)  (38.5 kJ/kg)) / ((70 kJ/kg)  (8.5 kJ/kg))
= 0.51
The total heat flow can be calculated as
q = (1 m^{3}/s) (1.205 kg/m^{3}) ((70 kJ/kg)  (38.5 kJ/kg))
= 38 (kJ/s, kW)
The sensible heat flow can be calculated as
q_{s} = (1 m^{3}/s) (1.205 kg/m^{3}) (1.01 kJ/kg.^{o}C) (30^{o}C  15^{o}C)
= 18.3 (kW)
According the Mollier diagram the specific humidity in (A) is 0.016 kg/kg and in (B) 0.0096 kg/kg and the latent heat flow can be calculated as
q_{s} = (1 m^{3}/s) (1.205 kg/m^{3}) (2502 kJ/kg) ((0.016 kg/kg)  (0.0096 kg/kg))
= 19.3 (kW)
Note! Due to inaccuracies when working with graphical diagrams there is a small difference between the total heat flow and the sum of the latent and sensible heat. Inaccuracies like this are in general within acceptable limits.
A similar cooling and dehumidifying process in the psychrometric chart:
 Transform between Mollier diagram and psychrometric chart
Related Topics

Air Psychrometrics
Moist and humid air  psychrometric charts, Mollier diagrams, aircondition temperatures and absolute and relative humidity and moisture content.
Related Documents

Air  Absolute Humidity
Absolute humidity is the actual mass of water vapor present in the air water vapor mixture. 
Air  Heating, Cooling, Mixing, Humidifying or Dehumidifying Processes
Basic air changing state processes  heating, cooling, mixing, humidifying and dehumidifying by adding steam or water  psychometric diagrams and the Mollier charts. 
Air  Humidifying by Adding Steam or Water
Air can be humidified by adding water or steam. 
Air  Humidifying with Steam, SI units
Using steam to humidify air. 
Air  Humidity Ratio
The mass of water vapor present in moist air  to the mass of dry air. 
Air  Maximum Moisture Carrying Capacity
Maximum water content in humid air vs. temperature. 
Air  Moisture Holding Capacity vs. Temperature
The moisture holding capacity of air increases with temperature. 
Air Conditioning  Cooling of Air and Condensate Generated
Water may condensate when air is cooled in air conditioning systems. 
Air Cooling of Storage Roooms
Heat removed from storage rooms with cooled air. 
Cooling Tower Efficiency
Maximum cooling tower efficiency is limited by the cooling air wetbulb temperature. 
Dehumidifiers
Classification of dehumidifiers. 
Dry Bulb, Wet Bulb and Dew Point Temperatures
Dry Bulb, Wet Bulb and Dew Point temperatures can be used to determine the state of humid air. 
Great Sensible Heat Factor  GSHF
The Great Sensible Heat Factor is the ratio sensible to total heat in a cooling coil. 
Heat Recovery Efficiency
Classification of heat recovery efficiencies  temperature efficiency, moisture efficiency and enthalpy efficiency  online heat exchanger efficiency calculator. 
Humid Air  Heating
Enthalpy change and temperature rise when heating humid air without adding moisture. 
Moist Air  Psychrometric Table for Pressure 29.92 inHg
Dry and wet bulb temperatures, saturation pressure, water vapor weight, specific volume, heat and more. 
Moist Air  Relative Humidity
Relative humidity in moist air is the ratio of partial vapor pressure to air pressure. 
Moist Air  the Mollier Diagram
The Mollier diagram is a graphic representation of the relationship between air temperature, moisture content and enthalpy  and is a basic design tool for building engineers and designers. 
Moist Air  Transforming the Mollier Diagram to a Psychrometric Chart  or vice versa
The relationship between the psycrometric chart and the Mollier diagram.