Pipe and Duct Systems  Total Head Loss
Major and minor loss in pipes, tubes and duct systems.
The head loss of a pipe, tube or duct system, is the same as that produced in a straight pipe or duct whose length is equal to the pipes of the original systems plus the sum of the equivalent lengths of all the components in the system. This can be expressed as
h_{loss} = Σ h_{major_losses} + Σ h_{minor_losses} (1)
where
h_{loss} = total head loss in the pipe or duct system
h_{major_losses} = major loss due to friction in the pipe or duct system
h_{minor_losses} = minor loss due to the components in the system
 Major Head Loss  head loss or pressure loss  due to friction in pipes and ducts.
 Minor Head Loss  head loss or pressure loss  due to components as valves, bends, tees and the like in the pipe or duct system.
Summarized Major Losses
The major head loss for a single pipe or duct can be expressed as:
h_{major_loss} = λ (l / d_{h}) (v^{2} / 2 g) (2)
where
h_{loss} = head loss (m, ft)
λ = DarcyWeisbach friction coefficient
l = length of duct or pipe (m)
d_{h} = hydraulic diameter (m)
v = flow velocity (m/s, ft/s)
g = acceleration of gravity (m/s^{2}, ft/s^{2})
Note!  the head unit is with reference to the density of the flowing fluid. For other units  like mm Water Column  check Velocity Pressure Head.
Summarized Minor Losses
Minor head loss can be expressed as:
h_{minor_loss} = ξ v^{2}/ 2 g (3)
where
Since the velocity  v  in equation (2) in general is related to the pipe or duct where the component is located, the sum of the minor losses in a pipe or duct can be expressed as:
Σ h_{minor_losses} = Σ ξ (v^{2}/ 2 g) (4)
The minor loss can be calculated by summarizing the minor loss coefficients  and multiplying the sum with the dynamic pressure head.
Total Head Loss in a Single Pipe or Duct
The total head loss for a single pipe can be calculated by using equation (1) and (3):
h_{loss_single} = λ (l / d_{h}) (v^{2} / 2 g) + Σ ξ v^{2}/ 2 g (5)
or
h_{loss_single} = (λ (l / d_{h}) + Σ ξ ) (v^{2}/ 2 g) (6)
Total Head Loss in Serial Connected Pipes
The total head loss in several serial connected pipes can be calculated by adding the total head loss in each pipe or duct. The total head loss can be expressed as:
h_{loss_serial} = Σ [(λ_{1} (l_{1} / d_{h1}) + Σ ξ_{1}) (v_{1}^{2}/ 2 g) + .. + λ_{n} (l_{n} / d_{hn}) + Σ ξ_{n}) (v_{n}^{2}/ 2 g)] (7)
for 1 to n serial connected pipes
Related Topics

Fluid Flow and Pressure Loss
Pipe lines  fluid flow and pressure loss  water, sewer, steel pipes, pvc pipes, copper tubes and more. 
Fluid Mechanics
The study of fluids  liquids and gases. Involving velocity, pressure, density and temperature as functions of space and time.
Related Documents

Equivalent Length vs. Minor Pressure Head Loss in Pipe and Duct Components
Minor pressure and head loss in pipes vs. equivalent length in tubes and duct systems. 
Fluid Flow  Hydraulic Diameter
Calculate hydraulic diameter for pipes and ducts. 
Pipe and Tube System Components  Minor (Dynamic) Loss Coefficients
Minor loss coefficients for components used in pipe and tube systems. 
Pressure Gradient Diagrams
Static pressure graphical presentation throughout a fluid flow system. 
Pressure Loss in Pipes connected in Series or Parallel
Calculate pressure loss in pipes connected in series or parallel. 
Pressure to Head Unit Converter
Pressure vs. head units  like lb/in^{2}, atm, inches mercury, bars, Pa and more. 
Pumps  Head vs. Pressure
Converting head (ft or m) to pressure (psi or bar, kg/cm^{2}) and vice versa. 
Pumps and Fans  Energy Equation and Head Rise
The energy equation can be used to calculate the head rise in pumps and fans. 
Steel Pipes Schedule 40  Velocity Head vs. Water Flow
Velocity head can be used to calculate minor pressure or head loss in fluid flow systems. 
Velocity Pressure Head
Dynamic pressure or velocity head.