Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications!

Chimney Sizing

Calculate chimney draft and required chimney area - online calculator.

The capacity of a chimney depends on the potential chimney draft - the pressure difference created by the inside and outside air temperature difference and chimney height - and the chimney area.

The pressure difference in the chimney pulls air and fuel gas from the boiler or fireplace through the chimney and out of the building.

Chimney Draft

The pressure difference or chimney draft can be expressed as:

dp ch = h (ρ o - ρ i ) a g (1)

where

dp ch = pressure draft in the chimney (Pa)

h = height of chimney (m)

ρ o = ambient outside density of air (kg/m3 )

ρ i = inside chimney density of air (kg/m3 )

a g = acceleration of gravity (9.81 m/s2)

Since the Ideal Gas Law states that

ρ o T o = ρ i T i

or

ρ i = ρ o T o / T i (2)

where

T = t + 273 = absolute temperature (K)

where

t = temperature (°C)

- (1) can alternatively be expressed as:

dp ch = h ( ρ o < - ρ o T o / T i ) a g

or

dp ch = h ρ o ( 1 - T o / T i ) a g (3)

Example - Chimney Draft

A 20 m high chimney operates with flue gas temperature 200 °C (473 K) . The outside temperature is 0 °C (273 K) . The density of the outside air is 1.292 kg/m3.

The draft in the chimney can be calculated with (3) as

dp ch = (20 m) (1.292 kg/m3 ) ( 1 - (273 K) / (473 K) ) (9.81 m/s2)
<

= 107 Pa

Chimney Area

The velocity of air and flue gas in a smaller furnace should not exceed 2 m/s . Design velocities of larger furnaces should not exceed 10 m/s .

Required chimney area can be calculated as

A = Q / v (3)

where

A = cross-sectional area of chimney (m2)

Q = volume of flue gases at chimney temperature (m3 /s)

v = velocity (m/s)

In general 1 kW boiler heat requires 1100 mm2 of chimney area.

Related Topics

• Combustion

Combustion processes and their efficiency. Boiler house and chimney topics. Properties of fuels like oil, gas, coal and wood and more. Safety valves and tanks.

Related Documents

• Chimney's Explosion Doors

Recommended size of explosion doors or draught stabilizers in oil fired installations.
• Chimney's Size vs. Boiler Power

The size of chimney vs. boiler's heat load.
• Chimneys - Roof Termination

Chimneys and single wall vents roof termination.
• Chimneys and Fireplace Sizing

Chimneys and fireplaces for stoves burning wood or coal as fuel.
• Natural Draft - Air Flow Volume and Velocity

Air flow - volume and velocity - due to stack or flue effect caused by indoor hot and outdoor cold temperature difference.

Search

Search is the most efficient way to navigate the Engineering ToolBox.

Engineering ToolBox - SketchUp Extension - Online 3D modeling!

Add standard and customized parametric components - like flange beams, lumbers, piping, stairs and more - to your Sketchup model with the Engineering ToolBox - SketchUp Extension - enabled for use with older versions of the amazing SketchUp Make and the newer "up to date" SketchUp Pro . Add the Engineering ToolBox extension to your SketchUp Make/Pro from the Extension Warehouse !

We don't collect information from our users. More about

We use a third-party to provide monetization technologies for our site. You can review their privacy and cookie policy here.

You can change your privacy settings by clicking the following button: .

Citation

• The Engineering ToolBox (2003). Chimney Sizing. [online] Available at: https://www.engineeringtoolbox.com/chimney-sizing-d_175.html [Accessed Day Month Year].

Modify the access date according your visit.

7.8.15

.