- Resources, Tools and Basic Information for Engineering and Design of Technical Applications!
Blade Pass Frequency noise generated by a fan can be very intense and varies with the number of blades and the rotation velocity.
Blade Pass Frequency noise level intensity varies with the number of blades and the rotation speed of the wheel and can be expressed as
BPF = n t / 60 (1)
BPF = Blade Pass Frequency (Hz)
n = rotation velocity (rpm)
t = number of blades
Example - Blade Pass Frequency of Fan
If a fan with
10 blades rotates with 2400 rpm - the Blade Pass Frequency - BPF - can be calculated
BPF = (2400 rpm) (10) / (60 s/min)
= 400 Hz
Note that the energy in the sound may be very high and annoying for the surroundings, especially for fans with few blades.
Be aware that the Blade Pass Frequency may not be visible in charts common for fans and that fan noise in general is documented in
Room acoustics and acoustic properties, decibel A, B and C, Noise Rating (NR) curves, sound transmission, sound pressure, sound intensity and sound attenuation.
Noise is usually defined as unwanted sound - noise, noise generation, silencers and attenuation in HVAC systems.
The sound generated by a fan depends on the motor power, the volume capacity, the static pressure increase and the discharged volume.
Sound power from sources like fans, jet engines, cars, humans and more.
Acoustic noise calculation procedure HVAC systems.
About the Engineering ToolBox!
We don't collect information from our users. More about
This page can be cited as
The Engineering ToolBox (2008).
Noise generated by Fans - Blade Pass Frequency (BPF) . [online] Available at: https://www.engineeringtoolbox.com/fan-blade-pass-frequency-d_1137.html [Accessed Day Month Year].
Modify the access date according your visit.