Boiler - Exhaust Velocity
|Boiler Configuration||Recommended Boiler Exhaust Velocity|
|Ducts at minimum load ||< 4.0 ||< 13 |
|Stack at minimum load ||< 5.0 ||< 16 |
|Boiler with one-step burner (on - off) ||5.0 - 8.0 ||16 - 26 |
|Boiler with two-step burner (high - low) ||10 - 15 ||31 - 49 |
|Boiler with modulating burner ||15 - 25 ||49 - 82 |
|To keep the surface free from soot the velocity should exceed ||3.0 - 4.0 ||9.8 - 13 |
Boiler house topics, fuels like oil, gas, coal, wood - chimneys, safety valves, tanks - combustion efficiency.
Search Engineering ToolBox
- the most efficient way to navigate the Engineering ToolBox!
About Engineering ToolBox!
We don't collect information from our users. Only emails and answers are saved in our archive. Cookies are only used in the browser to improve user experience.
Some of our calculators and applications let you save application data to your local computer. These applications will - due to browser restrictions - send data between your browser and our server. We don't save this data.