Engineering ToolBox - Resources, Tools and Basic Information for Engineering and Design of Technical Applications! Sound attenuation vs. change in duct size.
Sound attenuation when changing duct areas or dimensions:
dL = 10 log( ( 1 + A 1 / A 2 ) 2 / 4 (A 1 / A 2) ) (1)
dL = noise attenuation (dB)
A 1 = inlet area (m 2)
A 2 = outlet area (m 2)
Note! - valid only for sharp changes.
Example - Attenuation when changing the size of a duct
The attenuation of noise when the ratio between area before and after
Acan be calculated as 1 / A 2 = 5 -
dL = 10 log( ( 1 + 5) 2 / 4 (5))
= 2.5 dB Related Topics Noise is usually defined as unwanted sound - noise, noise generation, silencers and attenuation in HVAC systems. Related Documents Chamber sound attenuation. Search
Search is the most efficient way to navigate the Engineering ToolBox.
About the Engineering ToolBox!
We don't collect information from our users. More about
This page can be cited as
The Engineering ToolBox (2008). Change in Duct Area and Noise Attenuation. [online] Available at: https://www.engineeringtoolbox.com/duct-area-change-noise-attenuation-d_1408.html [Accessed Day Month Year].
Modify the access date according your visit.